PHASETREAT® 6208 and FLOCTREAT® 7874 provide consistent quality of discharge water
- Clariant Oil Services provided a production system analysis and solution for the operator
- Successful treatment resulting in no water discharge violations for several years
A major operator in the Gulf of Mexico had been experiencing intermittent overboard water problems. The field consisted of five platforms (A, B, C, D and E) that flowed total fluids to the main facility (also E), where the fluids were separated and the water discharged overboard.
Fluids from Platforms A and B flowed to C, and then pumped to Platform E. The process equipment on E consisted of a high and low pressure separator that was two-phased and flowed to a heater treater. At this point, the oil was sold and the water went to a small skimmer, then a float cell before discharging overboard. The fluids from D flowed into the separators on E, while the fluids from C went directly to the treater. Incoming temperatures were between 65oF and 80oF with 125oF at the treater.
The incumbent demulsifier was only effective when the temperature of the treater was above 110oF and had 30 minutes of retention time. Due to fluids from Platform C being pumped twice a day to the treater, the retention time would decrease and the temperature would drop to 105oF during pump start-up.
Clariant Oil Services Solutions and Value Delivered
At the request of the operator, Clariant Oil Services designed a demulsifier, PHASETREAT 6208, to solve the overboard water discharge problems. The product showed excellent oil and water separation at 80oF with 15 minutes of retention time.
PHASETREAT 6208 was injected into the incoming line from D on E, while the injection point for C was moved back to Platform C. This allowed Clariant Oil Services to lower the injection rate and take advantage of the pipeline shipment crude to break the emulsion before it entered the treater. Due to the emulsion being broken before it entered the treater, only a 5oF drop was noticed with very little change in water quality. A water clarifier from Clariant Oil Services, FLOCTREAT 7874, was used at the treater water dump outlet, making the skimmer and float cell more efficient and allowing for more consistent water quality.
Clariant Oil Services also was given the opportunity to introduce its paraffin inhibitor, WAXTREAT 3028, on Platform D, which showed significant performance increases over the incumbent.
This information corresponds to the present state of our knowledge and is intended as a general description of our products and their possible applications. Clariant makes no warranties, express or implied, as to the information’s accuracy, adequacy, sufficiency or freedom from defect and assumes no liability in connection with any use of this information. Any user of this product is responsible for determining the suitability of Clariant's products for its particular application.*Nothing included in this information waives any of Clariant’s General Terms and Conditions of Sale, which control unless it agrees otherwise in writing. Any existing intellectual/industrial property rights must be observed. Due to possible changes in our products and applicable national and international regulations and laws, the status of our products could change. Material Safety Data Sheets providing safety precautions, that should be observed when handling or storing Clariant products, are available upon request and are provided in compliance with applicable law. You should obtain and review the applicable Material Safety Data Sheet information before handling any of these products. For additional information, please contact Clariant.
*For sales to customers located within the United States and Canada the following applies in addition: NO EXPRESS OR IMPLIED WARRANTY IS MADE OF THE MERCHANTABILITY, SUITABILITY, FITNESS FOR A PARTICULAR PURPOSE OR OTHERWISE OF ANY PRODUCT OR SERVICE.
Copyright © Clariant International Ltd, 2012.